System settings specify the performance parameters, the depth of data storage in logs and their visualization, as well as additional functions - ModBus/TCP server, WebHMI Cloud
For the 4.0.7475 fw version, the following languages are available:
And you can select 'Autodetect' option too.
Specifies the period of data exchange with the connected devices. WebHMI reads all registers from all devices one by one. One such cycle is named scan. When possible WebHMI will insert delays between scans so they will run with specified interval.
A short interval increases the polling frequency, reduces the response when changing the register on the dashboard, and the 'response' of changes in the trends, but with a large number of interrogated data, they may not fit in the interval at the time, which will actually increase the scan, increase load on the system.
This settings should be set reasonably. If you need to 'have time' to query a large amount of data for a second, first you need to increase the speed of communication with devices, use the priority of reading the registers in conjunction with the option 'strict scan', do not read the auxiliary registers unnecessarily (use the read on-demand option for this).
This option allows to get a time-determined scan. It is usable for projects with hundreds and thousands of registers on slow serial connections.
If all registers fail to “fit in scan”, you can ask WebHMI read all important registers and a fraction of all other registers in every scan. This will allow update important registers much faster than others.
Critical registers should be given high priority in the register properties. And registers with normal priority should be set individually significantly longer polling time than the default scan interval. This will make WebHMI poll them less frequently and make Strict Scan feature possible.
WebHMI uses Comet technology to push register value changes into browser at the end of every scan where it was changed. Sometimes register value changes too often. To save traffic and resources you can throttle send interval. You can tell WebHMI send these update not often than some interval. This setting is adjustable between 100 ms. up to 5 sec.
Some devices’ OS, like smartTV, may report wrong resolution for the browser, lowering it for a convenient view. In most cases this is not desired behaviour in the monitoring systems, because the visualization is developed for the specific display resolution. Now you can force screen resolution to desired.
For some projects it makes sense to hide side menu. This option allows to hide menu by default.
There is a communicacion log to analyze system's behaviour using output messages:
This option sets the log's levels, possible values are:
Clear comm log from page
The amount of data in the communication log can sometimes become large, for example, when there are errors or when the trace mode is enabled. When searching for the required data block in it, sometimes it is necessary to clean the communication log, since it is constantly being overwritten (due to the size limitation). Now you can clear the communication log directly from its page, and not return to a separate menu.
This option sets the depth of storage of the stored data (logs of registers, events, data of graphs)
3 various actions on external power outage:
MobBus server - when turned on, allows external client to poll the project register using Modbus/TCP protocol. (see function description)